Unfortunately, I don’t have any spec as the UFH was installed by the builder’s heating guy and there was no design.
Do I need to turn down the flow meters to 2.5L when I only have the UFH on? Will that reduce the boiler cycling?
Need to get some temp clamps and get the individual flow and return temp differential on each set of white pipes to 5-7 dc on start up before the slab is hot eg when it’s had a day or two to cool
Won’t stop the boiler cycling due to ufh being let’s say 2kw and the min boiler kw to 6 etc