I'm testing the new ad network again, so you may have logging in issues - update me in THIS THREAD if you can't login or have the weird login issues again.
Welcome to PlumbersForums.net - The international free plumbing advice forum. Professional plumbers sharing advice with fellow plumbers and DIY alike. Register for free today! - Checkout the Plumbing Advice forum and then our Plumbing Videos area which still needs populating.
Probably got boiler running at lowest cycle. Be careful, legionella and waters to be stored @ 60 degrees.t te To be honest no ideas' ??
The immersion back up is probably set the right temperature, as for the blending its like the mixings taking place in the valve body and the hots the better...
Never do ever try twisting them thingys..would rather put trunks on and get in the tank and snorkels stick a plug in the ole.
Yes meant for these type systems..
Seems like its stuck open and spun off the spindle. So surprised these things still exist - and seen them in so many wrong places
So if I remember the heat - link is Linked common - Live on on the heat link to 1??
theres a call Puts Live down on 3 which is connected to the R room stat Link on boiler harness??
Might be wrong as the call on most combis the same..
Is wired like this?
THERE IS A NEUTRAL WIRE IN PLACE...
Frost stat set to #5 Boiler must of initiated the temperature being close enough 7 degs a bit close to BRRR +or- at the actual temp
When its cold and temperature reached boiler will function to prevent any freezing occurring.
Yes when Green lights out - no flames present at chamber - pump keeps...
Are ALL radiator TRV,s are turned UP to MAX or different settings in places?, hoping this,ll continue the heating to work after last shut down to dissipate. How many Rads on system?
Check the timer settings??
Sounds like a mixer valve blending issues - UNLESS you've a sealed or open vent type system and have booster pump added to boost your desire at the outlet??
If so ..
Could be again an unbalanced at controls at the time - depending on boost - what is boosted - if boosted?
If Balanced boost...
Personally if you've not had it looked at yet. Would ask you call megaflo / Heatrae Sadia to get one of their tecs round to have a look?
Depends? Levels?.. Wheres the bathroom and kitchen to where hot water cylinders sited?
What size is cylinder?
Saying that ,FLUKE is worth it. But their range is so HUGE and with the FLUKE 116 and its HVAC.
But Rally cant see a reason to purchase as I only do AC - resistance - continuity task.
Current meters a digital budget multi-meter - guys keep saying when you getting a FLUKE
Never knew I went on...
Any recommendations on the FLUKE 113..as know WAY am I going for the FLUKE 116 I keep hearing is the engineers multimeter.. REALLY??
113 Half the price and does the trick?
Think the only goodness is the FLUKE 116 is it has temperature. - NO NVC??