We're aware of an ongoing login issue, please use THIS THREAD to keep updated.
Welcome to PlumbersForums.net - The international free plumbing advice forum. Professional plumbers sharing advice with fellow plumbers and DIY alike. Register for free today! - Checkout the Plumbing Advice forum and then our Plumbing Videos area which still needs populating.
Quote below from the warranty section of the user manual. But, it was mentioned in this thread that in the UK softened water is not commonly used?
"Water is the intended heat-transfer medium. For
special anti-frost requirements, up to 30% glycol
may be added. Softened water is required for...
The original commissioning was overseen by an expert from the UK sole importers of ETA boilers, so I assumed that it had all been done properly.
As far as I am aware only standard mains water was used which is relatively hard in my area. Plus Trade-Chem inhibitor.
The problem prior to the power flush cleaning was the colour of the water - dirty brown, brown sediment in the bottom of the sample jar when left to settle, and a pH of 4.73. When the two Fernox TF1 filters were flushed the contents were dark black.
The problem now is that the pH is 6.0...
The cleaner was run with heat for around 2-3 hours.
The current problem is that I can't obtain the information as to how long the manufacturer recommends the cleaner should be run for (see above).
The power flush cleaning and refilling of the system with inhibitor was done by the original...
It's a biomass system with a 650 litre buffer tank and 100 metres of underground pipe to two properties. The circuit in question is separate to any radiator circuits, that is separated by heat exchangers.
Well, I have a situation this week that 50 litres of C100+ inhibitor added to fresh mains water of 6.7pH, tests at 6.0pH.
To me that suggests that the system may not have been completely flushed clean after using C600 power flush? Prior to the power flush the water was visibily brown rusty with...
Unfortunately I am constrained by the choice of chemicals already made by the supplier/installer of my biomass heating system. I am suspecting that the power flush conducted this week may not have been done properly, so I want to research both the power flush and inhibitor as thoroughly as...
Does anyone have access to the data sheets for Trade-Chem C100+ (C100S) inhibitor and Trade-Chem C600 power flush please? Also Trade-Chem step by step instructions on how to use the C600 power flush? I have been refused.